Volume 8, 2021
|Number of page(s)||6|
|Published online||19 July 2021|
Research on the electric field intensity distribution of high-voltage cable terminal improved by non-linear material
Electric Power Research Institute of State Grid Hebei Electric Power Co., Ltd., Shijiazhuang, Hebei 050021, China
* e-mail: firstname.lastname@example.org
Accepted: 22 June 2021
The electric field distortion caused by the high voltage current environment in the cable terminal will greatly increase the failure probability and reduce the operation safety; therefore, it is necessary to ensure the uniform distribution of the electric field in the terminal. This paper briefly introduced the high-voltage cable terminal and non-linear materials. The traditional silicone rubber and the silicone rubber added with nano-SiO2 were prepared. The electrical conductivity of the two silicone rubbers was tested, and the electric field of the cable terminal was simulated. The results demonstrated that the nano-SiO2 improved silicone rubber had a higher non-linear conductivity and was less affected by temperature. The calculation results of the simulation model also showed that the distribution of the internal field strength was more uniform, and the maximum field strength on the reinforced insulation was smaller after the improved silicone rubber was used as the reinforced insulation.
Key words: Cable terminal / direct high-voltage current / electric field intensity / COMSOL
© G. Li et al., Published by EDP Sciences 2021
This is an Open Access article distributed under the terms of the Creative Commons Attribution License (https://creativecommons.org/licenses/by/4.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.
Current usage metrics show cumulative count of Article Views (full-text article views including HTML views, PDF and ePub downloads, according to the available data) and Abstracts Views on Vision4Press platform.
Data correspond to usage on the plateform after 2015. The current usage metrics is available 48-96 hours after online publication and is updated daily on week days.
Initial download of the metrics may take a while.